I'm still working away on that little garage project I took on. Yesterday, I got the new gas boiler hung, got the vent and flue through the wall and ran gas to it. This afternoon, I'm going to get the utility sink picked up and start in on installing it.
Looking at how cars park, and where the doors swing, the utility sink needs to move as close to the electric subpanel as possible. Yet, somehow, I have a feeling there's a rule that limits this sort of thing. This is a 100 AMP subpanel. I'd like to mount the utility sink about 2 feet to the right of it. It would also be about 2 feet beneath it. Access to the panel isn't going to be a problem. All the plumbing is plastic, if that matters.
Any code on this? No one out here in the sticks is ever going to check it. Still, I'd just as soon follow the rule, if there is one.
Phil, I don't think you'll have any issues if I understand your question correctly. As long as the panel isn't block and has a clear, unobstructed space in front and below, you're fine IIRC, the number is I think 3 feet working space in front and the width of the panel to allow servicing. Don't have my code book handy. As far as oulets, they should all be on a GFCI outlet/breaker in a garage unless the outlet is dedicated specifally for something, such as a central vac, garage door opener, refrigerator, ect. You cannot use a conventional dupex outlet, meaning plugging in 2 devices into it. It needs to be a single style that will only allow one decive, similar to a clock outlet. Basically stated, there can't be anything in front or below the panel. Besides you already passed your final electrical inspection.
I think Tom's right. My code book is at work also but I think the 3 foot is fine. I can look it up in the Am but I sure more will chime in before I get a chance to look it up. 70 Sportsroof is an Elect. Eng and a lot younger than I :p , he might know as he does this all the time.
"Gun Control: The theory that a woman found dead in an alley, raped and strangled with her own pantyhose, is somehow morally superior to a woman explaining to police how her attacker got that fatal bullet wound."
I checked with my electrician buddy after church today and he agreed. No problems on the code with the panel. He mentioned the issue with GFI.
My buddy at church is a good resource, but I always need to check what he tells me. He did his apprenticeship on a battleship during dubbya dubba two. He's been retired long enough that there have probably been several changes to the code since he was involved on a day-to-day basis.
I thought there might be a more restrictive rule. When we installed the hot tub, the instructions said the disconnect had to be a minium of 6' away from the tub. I was afraid there might be something like that in the code...and in this case, I just don't have another 4-feet to move the sink. I'd just have to not install it if it came to that.
As far as electrical inspections? There are none in this area of the planet. I guess there's a potential the my insurance company might inspect it, but there is no building authority to do it. Not in this town. Not in this county. The way I look at it, just because it isn't going to be inspected doesn't mean it shouldn't be done right.
I think Tom's right. My code book is at work also but I think the 3 foot is fine. I can look it up in the Am but I sure more will chime in before I get a chance to look it up. 70_Fastback is an Elect. Eng and a lot younger than I :p , he might know as he does this all the time.
You need to have a 30" wide space in front of the panel, and the 30" clear space shall have a minimum clear distance of 36" for a nominal voltage to ground of 0 - 150V (i.e.: your scenario). basically a 30" wide space in front of your panel, extending out 36". And per code, the 30" width can be measure from either edge of the panelboard - it does not have to be centered.
Make sure no water piping, vent, etc runs directly above the "foot print" of the panelboard. You have to keep 6' above the panel clear of any "foreign" systems.
The AutoGuide.com network consists of the largest network of enthusiast-owned enthusiast-operated automotive communities.
AutoGuide.com provides the latest car reviews, auto show coverage, new car prices, and automotive news. The AutoGuide network operates more than 100 automotive forums where our users consult peers for shopping information and advice, and share opinions as a community.